TEPCO has released a video of the 8 minute trip into unit 3. We have some enhanced still images from the video.
Some noted information that has come out of the video:
The torus room door is bowed out both across the width and height of the door as if it either experienced considerable pressure or was struck by something.
Workers could not open the door even with attempts to kick it open.
Structures between the air lock door and the torus door had strike damage and large pieces of debris.
What looks like a pipe that has been moved about a foot away from original location.
Images below with notes, click on each image for larger view.
Unit 3 torus room door, line shows lower door bend
Unit 3, testing radiation at torus room door
Torus room door with bend
Temporary pipe held up with rope going into the MB (mezzanine basement)
Temporary pump controls with a camera on gauges in unit 3 MB
Unit 3’s torus room door, bowed out by handle. Door pushes in. Workers could not open door even with kicking.
Torus room door with red marks to show the arc of the vertical bow of the door.
Unit 3 torus room door. This image shows the outward dent in the door.
Overhead pipes in the MB near the stairs
Was this pipe dislodge from the mount nearby? This is near the torus room door.
Pipes near the stairwell. Horizontal sheet metal pipe on right has big dent.
Unit 3 going in to MB shows the volume of temporary hoses running in the buildings.
Near the torus room door. Pipe, what looks like a mounting bracket and open pipe in floor?
Looking outward at the MB stairwell airlock door, this area looks undamaged.
More ceiling area pipes and conduit in MB level
Large pipes coming out of floor in the MB area. The area has 2 of these.
Testing around the large pipe in the floor
Part of a stairwell rail and what looks like an open airlock door
Another view of pipes in floor in MB area
Large piece of crumpled debris in MB area
another view of the pipes coming out of the floor.
Water in the basement level of unit 3
testing water surface for radiation, basement stairwell
Airlock into the MB stairwell
MB airlock door can’t be closed due to temporary pipe run through doorway.
Sheet metal pipe near stairwell on MB level. Punctures deep enough to almost puncture the metal. Similar pock marks are
found on the stair treads and the nearby concrete wall.
This article would not be possible without the extensive efforts of the SimplyInfo research team
Join the conversation at chat.simplyinfo.org
© 2011-2016 SimplyInfo.org, Fukuleaks.org All Rights Reserved Content cited, quoted etc. from other sources is under the respective rights of that content owner. If you are viewing this page on any website other than www.simplyinfo.org (or www.fukuleaks.org) it may be plagiarized, please let us know. If you wish to reproduce any of our content in full or in more than a phrase or quote, please contact us first to obtain permission.